AWCI Technical Manual B, “Standard Practice for the Testing and Inspection of. Field Applied Thin-Film Intumescent Fire-Resistive Materials. Provides field inspection procedures for the testing of thin-film intumescent fire- resistive materials. Includes testing criteria for thickness measurement of applied . AWCI Technical Manual B, Standard Practice for the Testing and Inspection of Field Applied Thin-Film Intumescent Fire-Resistive Materials; an Annotated.
|Published (Last):||26 November 2005|
|PDF File Size:||2.47 Mb|
|ePub File Size:||14.28 Mb|
|Price:||Free* [*Free Regsitration Required]|
International Paint, LLC, which is located at: A concrete surface could be too slick because it has been coated with some kind of sealer, or the forms left a tight surface that was not roughed mankal or otherwise pretreated before the plaster was applied. Submit manufacturer’s written installation instructions. Factory manufactured architectural fire protection system will be a complete system from a single source consisting of primer, factory manufactured fire protection sections, section adhesive, edge sealant and decorative topcoat.
Patching must be performed by the qualified installer and applied in accordance with the manufacturer’s installation instructions. What is the intended pattern?
All products listed in this section must be manufactured under the appropriate follow-up service with each container bearing the certified label mark. To ensure a concrete surface is clean and rough enough to receive a stucco finish, it may need to be sandblasted or mechanically technica, a dash coat of the cement plaster mix can be applied 12-n the finish coat, or metal lath can be techncial using poweractuated fasteners implying a two- or threecoat stucco system to follow.
Clean substrate free of dust, dirt, grease or other foreign substances that would impair with the bond of the factory manufactured architectural fire protection adhesive material.
Verify that substrate and workspace temperature and humidity conditions are in accordance with requirements of this section.
SECTION ARCHITECTURAL INTUMESCENT FIRE PROTECTION
Architectural Fire Protection Installer: All surfaces to receive the factory-manufactured architectural fire protection material must be clean, dry and free of oil, grease, loose mill scale, dirt, dust or other foreign substances which technicxl impair bond of the architectural fire protection material to the substrate. In other words, the concrete can’t be too slick or too dry.
Requests for substitutions must be made 30 days prior to submittal and contain the full name of maunal product, descriptive literature, testing data collected from mznual consensus standard testing, data on past performance, manufacturer’s instruction for use and generic type. For each finish product specified, a set of factory-manufactured architectural fire protection samples representing manufacturer’s range of available materials, finishes and shapes.
Where necessary, cleaning or other corrections of the surfaces to receive the factory-manufactured architectural fire protection are the responsibility of the installer of the incompatible substrate. Interchar can provide fully fire proofed steelwork without the need to topcoat.
Packaged materials must bear the appropriate labels, seals and designated certification mark for fire resistive ratings. Prior to mixing Part A and B of the adhesive and edge sealant during the installation of the architectural decorative fire protection material, random pre-determined liquid samples of Part A and Part B must be submitted for material characterization fingerprinting in accordance with the procedures 12-bb in the ISO Standard.
Technical Manual 12-B
A copy of the transport document and manufacturers conformance certificate shall be attached to the material delivery QC form. At project closeout, provide to Owner or Owners Representative an executed copy of the manufacturer’s standard limited warranty against manufacturing defect, outlining its terms, conditions, and exclusions from coverage.
Verify that all clip hangers, piping, ducts, equipment or other items which would interfere with the installation of the factory-manufactured architectural fire protection system are not positioned or installed until installation is complete.
Regional Materials- 20 percent extracted, processed and manufactured regionally: Temporary protection and heat shall be maintained at this minimum temperature for 24 hours before, during and 24 hours after material application.
International Protective Coatings is the leading supplier of high performance Protective Coatings and forms part of Akzo Nobel, a market driven, technology based company specializing in Coatings, Chemicals and Pharmaceuticals. Structural steel and framing with reference to primer receiving fire protection materials.
Provide ventilation in areas to receive work of this section during application and minimum 24 hours after application.
Equipment and installation procedures must conform to the factory-manufactured architectural fire protection manufacturer’s installation instructions. A pair of measurements 12 inches apart on a given beam in no particular, random location along the beam — the tested area could be near an end or in the middle of the span. So, one might wonder, how many beams or other structural members per test? Interchar is primarily a spray applied material, and performs without the requirement for any reinforcement.
Do not commence installation of the factory manufactured architectural fire protection system until the contractor, installer and inspector have examined the surfaces to receive the fire protection and determined the surfaces are acceptable to receive the fire protection material.
All batch number, product identification and quantities shall be recorded on appropriate QC documents. Each layer of portland cement plaster that is applied to the concrete should be damp-cured to prevent drying too quickly. No intumescent fireproofing or coating material may be procured or delivered to the project site prior to the review and acceptance of the proposed materials by the Architect in writing.
The factory manufactured architectural fire protection material aci supplied at the required dry film thickness in accordance with the appropriate design listing. Submit applicator’s current certification as a manufacturer trained and approved installer. There are several diagrams in B, but they are cross-sections of a beam, a column, a tube and a truss; the cross section of the beam includes arrows indicating the nine points around the beam where the film thickness of the TFIFRM is manuak be measured.
After several failed attempts to explain this testing procedure to me I first took it to mean one must measure near each end of the beam, 12 inches inthe technical sales rep wound up drawing a diagram that finally made it clear. A stand-alone reading of section 6. Install factory-manufactured architectural fire protection material only to primed surfaces and in accordance with manufacturer’s installation instructions. The application must be witnessed by the Architect’s or Owner’s representative and is subject to their approval.
Grind smooth all weld spatter and defects prior to commencement of fire protection installation. Store and dispose of hazardous materials, and materials contaminated by hazardous materials, in accordance with requirements of local authorities having jurisdiction. Techhnical claim that the instructions mean that the sample beam must be tested 12 inches from the end s of the aeci. Company specializing in manufacturing products listed in this section with a minimum of ten years documented experience.